Total views : 261
Experimental Analysis of Horizontal and Vertical Buried Tube Heat Exchanger Air Conditioning System
Objectives: In this paper, the analyses of Vertical and Horizontal Buried Tube Air conditioning system have been done. The dimensions for optimum performance from the CFD simulation are found. The comparison of the performance of vertical and horizontal Buried tube heat Exchange air conditioning system is included. Methods/Statistical Analysis: CFD simulations were carried out for optimised dimensions of Buried Tube Air conditioning system. In second part of this paper, researcher presented the installation of actual horizontal and vertical Buried Tube Air conditioning system with the help of simulation results at specific region of Gujarat, India. Horizontal buried tube heat exchanger requires more installation area with dry soil. Vertical buried tube heat exchanger is installed from the analysis of simulation results. Pipes of specific diameter and thickness were buried in bore with special type of arrangement. Findings: Horizontal buried tube heat exchanger comprises of horizontal pipe of 0.104 m inner diameter with buried Length of 25 m, made up of RCC and buried at a depth of 3 m in a flat land whereas Vertical buried tube heat exchanger with 110mm diameter and 6mm thickness were buried in the bore of 610mm diameter and 8m depth with special type of arrangement. In the end researcher represented the actual results in context of performance, comparison of simulating and actual results with suggested best the design and loop of heat exchanger for optimum performance. The results also present the dimensions of Buried tube air conditioning system for producing optimum human comfortable condition. The accuracy of this Experimental setup has been verified by comparisons of temperatures of the air and soil and the performance between simulation results with the test data. Applications/Improvements: Vertical and Horizontal Buried tube heat exchanger are used as Buried tube air conditioning system. It can be used for cooling purpose in summer and for heating purpose in winter. It is also useful to handle the green house thermal loads.
Buried Tube Heat Exchanger Air Conditioning System, CFD Simulation, Horizontal BTHE, Heating and Cooling System, Vertical BTHE.
- Antinucci M, Fleury B, Asian LJ, Maldonado E, Santamouris M, Tombazis A, Yannas S. Passive and hybrid cooling of buildings-state of art. International Journal Solar Energy. 1992; 11(3-4):251–72.
- Patel RD. Head Mechanical Engineering, BBIT and Head Mechanical Engineering, SVIT, Earth Appropriate Temperature for Buried Tube Heat Exchanger in Indian Climates, National Conference on Innovative Trends in Mechanical and Aerospace Engineering. 2014; 35(8):1–4.
- Bansal V, Misra R, Agrawal GA, Mathur J. Performance analysis of earth–pipe–air heat exchanger for summer cooling. Energy and Buildings. 2010; 42(5):645–648.
- Benkert ST, Heidt FD, Schöler D. Department of Physics, University of Siegen, Calculation Tool for Earth Heat Exchangers GAEA. 1997. p.1–8.
- Dubey M, Bhagoria JL, Atullanjewar A. Earth Air Heat Exchanger in Parallel Connection. International Journal of Engineering Trends and Technology (IJETT). 2013; 4(6):1–5.
- Jalaluddin J, Miyara A. Thermal performance investigation of several types of vertical ground heat exchangers with different operation mode, Applied Thermal Engineering. 2012; 33-34:167–174.
- Dubey M, Bhagoria JL, Atullanjewar A. Earth Air Heat Exchanger in Parallel Connection. International Journal of Engineering Trends and Technology (IJETT).2013; 4(6):1–5.
- Gao J, Zhang X, Liu J, Li KS, Yang J. Thermal performance and ground temperature of vertical pile-foundation heat exchangers: A case study. Applied Thermal Engineering 2008; 28(17-18):2295–2304.
- Kalidasan B, Ravikumar M. Numerical analysis of compact heat exchanger for flow distribution. Indian Journal of Science and Technology. 2016 Feb; 9(6):1–5.
- Nirmala R, Rajkumar R. Finite element analysis of buried UPVC pipe. Indian Journal of Science and Technology. 2016 Feb; 9(5):1–5.
- There are currently no refbacks.
This work is licensed under a Creative Commons Attribution 3.0 License.