Total views : 232
A Power Quality Survey on a 22 kV Electrical Distribution System of a Technical Institution as per Standards
Objective: Electrical power delivered to a load must be of sufficient quality to allow the load to function properly. Source side voltages and currents must be distortion free and of the proper magnitudes and frequencies. Critical equipment may undergo failure if quality power is not provided. So, the electrical voltages and currents flowing through our distribution system has to be monitored and analyzed to ensure quality power and thus proper working of the machineries in a technical institute. This paper presents a Power Quality Survey in a technical institute as per Standards. Methods: A Power Quality Survey has been conducted and the measured parameters are compared against Standards. Simulation study of the complete system is conducted using ETAP 12.5.0 software, so as to understand the existing load flow and harmonic profile. Findings: Current and voltage harmonics was found to be within the limits at PCC. Improvement: Harmonic profile of UPS-Academic block improved, when the old UPS was replaced with a modern numeric UPS.
Point of Common Coupling, Power Quality, Total Harmonic Current Distortion, Total Harmonic Voltage Distortion.
- Jain S, Agarwal P, Gupta HO. A survey of harmonics: Indian scenario. Proceedings of the IEEE INDICON; 2004 Dec. p. 84–9.
- Prabaakaran K, Chitra N, Senthil Kumar A. Power Quality enhancement in microgrid - A survey. IEEE International Conference on Circuits, Power and Computing Technologies (ICCPCT); 2013 Mar. p. 126–31.
- Ignatova V, Villard D, Hypolite JM. Simple indicators for an effective Power Quality monitoring and analysis. IEEE 15th International Conference on Environment and Electrical Engineering (EEEIC)); 2015 Jun. p. 1104–8.
- Mack GW, Santoso S. Understanding power system harmonics. IEEE Power Engineering Review. 2001 Dec; 21(11):8–11.
- Gosbell VJ, Perera S, Barr R, Baitch A. Primary and secondary indices for Power Quality (PQ) survey reporting. IEEE 11th International Conference on Harmonics and Quality of Power; 2004 Sep. p. 419–24.
- Ribeiro PF. Common misapplications of the IEEE 519 harmonic standard: Voltage or current limits. Power and Energy Society General Meeting-Conversion and Delivery of Electrical Energy in the 21st Century; 2008. Jul. p. 1–3.
- There are currently no refbacks.
This work is licensed under a Creative Commons Attribution 3.0 License.